Gradual substitution of the pumps of the Jaira pumping station - CCRR El Porvenir (altitude water transfer Tagus-Segura).
* 1 Unit High-flow rate vertical pump Mod. FEL60 + head + 2 units Sections 1489mm + strainer
* 1 Unit Motor B5 4P 850 HP 1800 m³/h at 100 mWc
The equipment is currently operating above its working point calculated at 3%, without vibrations and with correct temperature levels on bearings and coils.
It is operating and has an energy consumption 2% below the motor nominal value.
After installing the pump, the higher energy efficiency of the equipment and the greater hydraulic performance of the pump have been ascertained; thus the owners have already recovered the investment in the installation.